Question about Goodman CLQ36AR49 Air Conditioner
I have a 4yr old GMS9/GCS9 furnace and a GSC130361D condensing unit. The problem is when we call for cooling the fuse on the integrated control module blows yet I can run the furnace or the fan and it fine. Any suggestions?
Disconnect the the red and the yellow wires at the outdoor unit. Then replace the fuse and turn on the power.......see if the fuse blew. If the fuse blew, your problem is most likely a short in the low voltage wiring. Check for crimped or damage wire or wire insulation and repair as necessary. If the fuse is okay, then the problem is within your outdoor unit.......again inspect all wiring for any damaged insulation or crimped wiring.
Check these items and let us know.....we can guide you further after you perform these checks. :-)
Posted on May 26, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 27, 2013 | Goodman GMS90703BXA Heater
Apr 24, 2013 | Goodman GMS90703BXA Heater
Apr 04, 2012 | Goodman Heating & Cooling
Apr 04, 2011 | Goodman Heating & Cooling
Jul 16, 2010 | Goodman GMS90703BXA Heater
Apr 13, 2010 | Mastercool 67471 Evaporative Cooler Air...
Jan 02, 2010 | Goodman GMS90703BXA Heater
Feb 23, 2009 | Goodman GMS90703BXA Heater
Jan 28, 2009 | Goodman GMS90703BXA Heater
May 01, 2008 | Heating & Cooling
167 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: