Question about Carrier 38CKC036 Air Conditioner
I purchased a Dayton Motor (4M205G), and a Dayton capacitor (MPP2505370J) and I need to confirm the proper wiring setup to the capacitors and contactor. I have a 1.5 pole 30 amp 24VAC Definite purpose contactor from Mars.
Currently my compressor will not start, but I think I have something miswired.
The 2 brown wires to the cap in first legend is how they are wired electrically,inside that motor the run winding is common to that brown one they cappped off in the 2nd option, but the powers still going to Run.ommon and run get the juice either way, its just another way to do it, but electrically as to sides of power and where they go is no different, just different way to do it.you can run power in on the Run terminal on the run cap, the run winding and run cap and start cap if equipped are Run to Run to Run.So the hot leg for the run winding also goes to run on the caps, run to run to run.,run winding to run cap to run on start cap.
Posted on Feb 24, 2012
You do.I too have a Dayton replacement motor.Works great.
Posted on Jun 06, 2009
Probably the run capacitors mis-wired. if you can send me a photo maybe i can help you firstname.lastname@example.org
Posted on Apr 21, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 28, 2014 | Carrier Heating & Cooling
Nov 26, 2013 | Carrier Heating & Cooling
Sep 07, 2011 | Heating & Cooling
Aug 05, 2011 | Dayton Heating & Cooling
Apr 26, 2011 | Carrier 38CKC042 Air Conditioner
Sep 01, 2010 | Carrier 38CKC060 Air Conditioner
Jul 17, 2010 | GE 18 Hp Capacitor Start Ac Motor 115...
Apr 15, 2010 | Carrier Heating & Cooling
May 11, 2009 | Carrier 38CKC036 Air Conditioner
Jun 25, 2014 | Carrier 38CKC036 Air Conditioner
Jun 13, 2014 | Carrier 38CKC036 Air Conditioner
1,635 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: