- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
Is this a heat pump? Look in the thermostat. You should have something like the following.
Red wire to R terminal
Green wire to G terminal
Yellow wire to Y terminal
White wire to W or W1
Blue or Orange wire to the O or B terminal
Brown wire to C terminal.
Let me know what you have in the thermostat. The wire colors are not always the same.
you probably purchased a 4 wire thermostat which we call heat/cool you stated you have 6 wires which signifies a heat pump you have to purcahase a heat pump thermostat and then write down the color of the wires to there related spots example...yellowe-y red-r white- w and so forth also before you do this kill the power the voltage typical for residential is only 24v's but if the wires touch you could blow a fuse
Motor1258, Thanks for the response, to be more specific, the nine pin connector was damaged, but I was able to connect the wires back to main unit panel. I am ready to hook to the hunter thermostat and do not know which wires to connect to. This is my problem and I do not want to short something out. Hope this helps, I want to get it installed again. Thanks again for caring....Jerry