Question about Heating & Cooling
I have a Totaline digital thermostat for a Carrier A/C unit. Some of the wires were disconnected and I can't get them reconnected to have the outside condenser unit turn on automatically when the air handler and fan turn on. The condenser turns on when I put the red wire in the "R" position. Should it be placed somewhere else, perhaps the Y2 spot? I am afraid to try this for fear of permanent damage. Thank you for your help.
Call a technician
check all indoor n out door wiring of unit
if u do wronge connection wireing of unit may be burn
Posted on Apr 05, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 11, 2013 | Heating & Cooling
May 28, 2012 | Carrier Totaline P291-1003 Capacitor 10mfd...
Jul 10, 2010 | Carrier Heating & Cooling
May 03, 2010 | Honeywell Electronic Programmable...
Sep 13, 2009 | Heating & Cooling
Apr 27, 2009 | Whirlwind FH-778 Air Conditioner
Nov 23, 2008 | Ruud UBHC Air Conditioner
Jun 23, 2008 | Carrier Heating & Cooling
Nov 25, 2007 | Honeywell CT3600 7 Day Electronic...
143 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: