I have a Goodman mfg inside system that recently has failed to start the blower when the AC comes on. The outside compressor will start but the inside fan will not start every time. Some times it will and other times it will not. When I manually turn the fan on the samething occurs where it will come on sometimes. If I turn on the fan manually or wait until the AC system is to start based on the thermostat setting and the reset the breakers on the inside unit (Goodman Model A49-20) then the blower starts up and will run until it is shut down. It is very interminent on it not starting.
When the system is in heat mode the blower starts every time.
This should have a time delay sequencer for the blower in the a/c mode. These are bad about being interminent in the a/c mode and also in fan. I have had some that would freeze up and I would get there and the fan be running. Thaw out and check and everything be ok. Got to cycling the fan on and off and sooner or later it would get where fan didn't come on. After replacement the customer didn't have anymore problem. Check the rely, looks like a heat sequencer but mounted on plate to blower compartment.
An expert who has achieved level 3 by getting 1000 points
An expert that got 10 achievements.
An expert that got 5 achievements.
An expert who has achieved Level 3.
Re: Inside blower not starting every time
That's a weird problem. I wonder if the outside compressor is drawing down the voltage in the breaker box enuff to keep the blower from starting up. If you're set to cool but the thermostat is NOT calling for the AC, can you manually turn the blower on fathfully? If so, I would check all wiring connections in the breaker box to make sure they are tight and free from tarnish or corrosion. You may even need to contact your power company and have a higher amperage line installed outside. Do your house lights blink noticably when the compressor kicks on?
While you're resolving this, you could start the blower manually and just leave it on. The compressor cycling on/off shouldn't stop the blower once it's running and it won't draw much current... couple bucks a month maybe.
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need. goodluck!
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
Replace the blower motor resister,this is the speeds for the blower motor,it is located very near the blower motor,and is mounted on the blower box,and it actually goes inside the box,to keep it cool.The reason for it`s failure is the blower motor,even though the blower motor sounds,and runs good,it is drawing too many amps.If this was at all helpful,please rate,thank you.
Easy: Turn the "fan" switch to on at the thermostat and see if the blower starts. If no start, check breaker at breaker box. Check service disconnect at or near the air handler. With the breaker and/or service disconnect OFF check the 3 or 5 amp fuse inside the top cover in the air handler. Not so easy: (You must know what you are doing for this part or let an HVAC Tech do it for you) Open thermostat and firmly jump the Y and R terminals to see if you get the compressor to start for no more than 30 seconds. (don't do it more than once.) Jump the G and R terminals to see if you get the blower to start. If so, u have a bad thermostat. If not, check the transformer inside the same cover in air handler for proper voltage. (24V. Make sure you also get 220 on the opposite side of the transformer) If the blower comes on, but the heat pump doesnt start, open the side cover of the heat pump, with the thermostat on cool, and the temp. setting as low as possible for at least 10 minutes see if the contactor is pulled in. If so, check the capacitor and see if it's blown out. Be super careful these systems operate with 220v and the amperes are enough to kill you if you make a simple mistake.
You have a voltage bleed somewhere or a short, whatever you want to call it. Do you have a control board on this unit where the relays are integrated into it or do you have the old type where the relay is separate? Anyway, you need to take a meter and take voltage readings to the motor when it's acting up and when it's running right. I have had the same problem with a Goodman unit before and it turned out to be the tstat! What I would do is remove the cover off the tstat and take a small jumper wire and touch the r terminal to the y terminal. If the motor starts right up, you know it's the tstat. If you have the same problem, then the only thing it can be is a low voltage short to the unit from the tstat, bad control board if you have one, or a bad relay. But if the unit is working fine in heat, it's probably not the relay. I hope this helps.
Most motors have a thermal cut out that is internal. If the motor overheats, it will shut down. If the unit is freezing up, that would indicate that there isn't enough airflow over the coils or the unit is low on refrigerant. I had a unit that did this same exact thing and after replacing the blower motor and a sequencer, in the end it was the t-stat. You are describing the same exact symptoms and every time I would go out, the unit would work fine. I would suggest replacing the t-stat and then watch the unit. But make sure that the coils are clean and you are not restricting airflow over the coils. Hopefully one of the techs actually looked at the coils to determine if they needed to be pulled and cleaned. Hopefully this answers your question.
you should not need the owners manual. most likely you will find a chart listing the diagnostic codes on the inside of the door to the blower compartment. diagnostics are printed next to the wiring schematic. the most common problem on this style furnace is just a dirty flame sensor. a small piece of fine grit sandpaper and a 1/4" nutdriver is needed. the sensor is located in front of the burner on either the far left or right. be carefull....(do not remove the hot surface ignitor that has two wires). you want the part that has only one wire connected to the sensor under the buner. pull it out and sand the dirt off of the metal rod. reinstall and enjoy your heat
Actually you might get a ohm meter the reads to at least 40 megaohms and check the coil on the solenoid valve as well as the coil on the contactor. That would determine which coil ic failing. They should read out above 40 megaohms.