Question about Carrier 38CKC036 Air Conditioner
I had to replace a fan on my carrier unit and I did not mark the 3 wires I disconnected for the fan. One yellow, one brown, and one black. I know the yellow connects with the other yellow wires on the capacitor and I think the black goes to the output side of the power block and the brown to the other side of the capacitor, but I am not sure of these two connections.
Should be OK to hook it up and try it, make sure the fan is blowing out, if not, reverse the wires..
Posted on Apr 04, 2008
There should be a wire diagram on your service pannel locate the fan wiring and and you will find your answer.
Posted on Jun 15, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 26, 2013 | Carrier Heating & Cooling
Jun 22, 2012 | Carrier Heating & Cooling
Jul 25, 2011 | Heating & Cooling
Jul 13, 2010 | Heating & Cooling
Apr 05, 2010 | Heating & Cooling
May 31, 2009 | GE Heating & Cooling
Feb 21, 2009 | Carrier Heating & Cooling
Aug 25, 2008 | Goodman CKL60AR60 Air Conditioner
Aug 14, 2008 | Carrier Heating & Cooling
Jul 18, 2008 | Carrier 38CKC036 Air Conditioner
Jun 25, 2014 | Carrier 38CKC036 Air Conditioner
Jun 13, 2014 | Carrier 38CKC036 Air Conditioner
108 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: