Question about Samsung AQ24 Air Conditioner
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You need four wires(two #10 and two #12) to the outdoor unit, leaving you house, and three wires(#10) coming from the breaker to tye indoor unit inside your house.
Split A/C-Cold and Hot:
You need five wires(two #10 and three #12) to the outdoor unit, leaving your house, and thee wires(#10) coming from the breaker to your indoor unit inside your house.
This ypical arrangment(all of them use three wires fro the breaker), yet there are other units which may require 6-7 wires connected to the the outdoor unit depends on the added features to the unit.
Posted on May 02, 2009
The outdoor unit should have 2 small wires connected to the contactor coil. This delivers the 24v "Signal" to energize the coil. The wire from the t'stat for cooling are usually yellow, in almost every case. When you put the t'stat in the cooling mode and set the temp lower than the room temp, the indoor and outdoor unit should come on. Check for voltage on the terminal block for 24 volts accross the yellow and common wire. Common could be ground on some handlers. If you have the 24 volts, then check for 24v on the 2 small wires (usually 18 to 22 gage wire) on the contactor coil. If no voltage, trace the 2 wires back to the indoor unit and see where they go. If they are the ones that are not attached, put one on the yellow wire terminal and the other on the common terminal. This will send power to the indoor unit and then piggyback to the outdoor unit. Do not remove the yellow and common from the terminal block. Don't be too concerned about the colors from the outdoor coil wires. Just make sure they are hooked up right. Good Luck and hope this gets it going.
Posted on Jun 07, 2009
Tips for a great answer:
Apr 19, 2017 | Samsung Heating & Cooling
Aug 22, 2011 | Carrier 38CKC042 Air Conditioner
Feb 08, 2011 | Heating & Cooling
Feb 03, 2011 | Mitsubishi Heating & Cooling
Jan 30, 2011 | Mitsubishi Mr. Slim MXZ30TN Air...
Jan 19, 2011 | Heating & Cooling
Jan 16, 2010 | Panasonic Heating & Cooling
Sep 30, 2009 | GE Quiet-Aire Ductless Split System Air...
• Wrong or missing wiring between indoor and outdoor unit cable
• Defect of communication components in indoor pcb assembly
• Defect of communication components in outdoor pcb assembly
• Defect of power supply components in outdoor pcb assembly
• No ground connection in air conditioner unit
(affected by noise in power source)
Jun 30, 2009 | LG Heating & Cooling
May 14, 2009 | Heating & Cooling
68 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: