Question about Heating & Cooling
Posted by Anonymous on
The 265/277v units will not work in a 208/230v hotel without a transformer. Basically you do not want to get involved with that. When replacing your PTACs stick with the proper voltage. As far as a conversion kit, if one exists, the cost will put you right back at the cost of a new unit. If your hotel is wired for 208/230v it won't give the unit the power it needs to function properly. When looking for replacement units here's what you need to match (besides getting the proper BTUs):
Unit size (make sure they fit in your existing sleeves)
Power cord configuration (the 265/277v will have a different power plug)
Posted on May 26, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 30, 2015 | Amana PTC123G35AXXX DigiSmart Series 11...
Dec 12, 2013 | GE Zoneline Deluxe Series Cooling &...
Feb 02, 2013 | Amana In Wall Install Kit For Digismart...
Aug 31, 2012 | Amana PTH123B50AJ Heat Pump,12000BTU,...
Sep 06, 2011 | LG LP126HD3A Air Conditioner
Aug 14, 2010 | Heating & Cooling
Mar 26, 2010 | Heating & Cooling
Nov 23, 2009 | Electronics - Others
Aug 11, 2009 | Amana PTH123B25AJ Heat Pump Air...
95 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: