Question about Heating & Cooling
Posted by Anonymous on
Try the least exspensive thing first an thats the thermostat,then if you are firmiliar with the parts on a centrall system look at the stamatic for the location of the high limit control if its an older system,an an an then with the new system check relays on board
Posted on May 16, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Most likely cause would be a 'stuck' sequencer. The sequencer will be similar to the one in the pic below. Luckily, they are relatively cheap (about $20).
Posted on Mar 26, 2010
Tips for a great answer:
Dec 24, 2016 | Heating & Cooling
Nov 06, 2010 | Coleman Mach III Air Conditioner
Mar 25, 2010 | Goodman Heating & Cooling
Jan 12, 2010 | Carrier 38CKC042 Air Conditioner
Dec 24, 2009 | Coleman Mach III Air Conditioner
Mar 11, 2009 | Coleman Heating & Cooling
Nov 12, 2008 | Intertherm Heating & Cooling
23 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: