Question about Heating & Cooling
. is the flame detection probe or its wiring harness, this sits right on the heat ex and over time melts and sticks to the heat ex so looses continuty.
To check if the detection probes faulty, get a multimeter pull the wiring off the probe stick one end of multimeter on probe connection, other end to the wiring plug, set your multimeter to mirco volts. fire boiler up. you want more than 1.5MV's or probes is knakered! Check continuity of wiring, also check wiring is full pushed in to the white molex connector too.
Posted on May 14, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 19, 2014 | Water Heaters
Nov 24, 2013 | Heating & Cooling
Mar 16, 2011 | Heating & Cooling
Mar 04, 2011 | Desa International CBN30T Central Heating...
Nov 13, 2009 | Sony PFM-42B2 42 in. Plasma HDTV
May 28, 2009 | Frigidaire Dryers
127 people viewed this question
Usually answered in minutes!