Question about Goodman GMS90703BXA Heater
There can be several reasons your not igniting. You may have a dirty filter, safety switch engaged etc. There is a diagnostic light in the bottom compartment that flashes a code. see what code it is flashing and post that info. The breakdown for the code is on the back of your door.
Posted on Mar 29, 2008
Tips for a great answer:
Nov 08, 2012 | Goodman GMS90703BXA Heater
Jan 04, 2011 | Heaters
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remaing solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the igniter. The igniter will glow and you will be able to see it if viewed thru the small inspection port. Once the igniter gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the igniter does not energize (bad control, bad igniter), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not light (dirty pilot), the burner does not light (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Oct 05, 2010 | Goodman GMS90703BXA Heater
Feb 26, 2010 | Mr. Heater Natural Gas Garage Heater -...
Feb 16, 2010 | Dayton Gas Furnace Heater
Feb 12, 2010 | Goodman Heaters
Jan 28, 2010 | Heaters
Jan 26, 2010 | Goodman Heaters
Jan 06, 2010 | Goodman GMS90703BXA Heater
Jan 04, 2010 | Coleman Propane Forced Air Heater...
213 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: