Question about Goodman GMS90703BXA Heater
It is for sure a venting issue, depending on where you are located, it sounds like the local building code inspector was not involved for an inspecton of the furnace replacement. When the flue condensates like that, it is usually because the flue is the wrong size, usually to big,or it is dumped directly into a masonary chimney, and the chimney was not lined to the top.
I hope this answers your questions, please rate me and let me know if I can help further.
Posted on May 13, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 13, 2016 | Dayton Heating & Cooling
on Dec 14, 2009 | Heating & Cooling
Dec 10, 2013 | Heating & Cooling
Mar 08, 2017 | Goodman Heating & Cooling
Oct 20, 2011 | Intertherm P3RA-048K Air Conditioner
Nov 06, 2009 | Coleman Propane Forced Air Heater...
Nov 03, 2009 | Goodman GMS90703BXA Heater
Jan 26, 2009 | Heating & Cooling
Oct 14, 2008 | Carrier Heating & Cooling
110 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: