Question about Heating & Cooling
Carrier 58SS Clicking Sound The furnace runs. However it is making an intermittent sound that appears to be coming from an area that according to a pdf of the furnace contains the Gas Control Dial and the Gas Control Valve. The noise it makes sounds like a clicking noise or a dial turning. When it makes this sound the burners will diminish a bit and then come back on full force. We had a professional come out yesterday but since it wasn't making the noise when he was here he wasn't sure what the problem was. If you look at the pdf of the furnace the noise sounds like it's coming from #3 and #9 on the diagram. Here's a link to the pdf: http://www.docs.hvacpartners.com/idc.../58ss-2p~1.pdf We're wondering if anyone might have an idea what is going on? Thanks very much.
Posted by Anonymous on
Measure the voltage to Terminals #2 and #3 on the main gas valve. If the voltage remains consistent while you hear the sound and the burners diminish slightly, the problem will be your main gas valve. If the voltage fluctuates, you will have to trace it back through the wiring to see through which switch you are losing it.
If this furnace has a hot surface ignitor with flame sensor, try cleaning the flame sensor with some emory cloth.
I hope you find this information to be very helpful as a good starting off point for you.
Please leave a rating. :-)
Posted on May 14, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 16, 2017 | Cars & Trucks
Jun 18, 2013 | Dometic Rooftop RV Air Conditioner
Jan 03, 2013 | Heating & Cooling
Jan 02, 2013 | Carrier Furnace Control Circuit Board...
Oct 23, 2010 | Heating & Cooling
Mar 19, 2010 | Heating & Cooling
Jan 03, 2010 | Dayton Gas Furnace Heater
Apr 05, 2009 | Intertherm P3RA-048K Air Conditioner
Mar 11, 2009 | Carrier Heating & Cooling
Sep 21, 2017 | NewAir Heating & Cooling
401 people viewed this question
Usually answered in minutes!