Question about Bryant Heating & Cooling
Have you used the weed eater out by the condensing unit could be short in thermostat control wiring to outside unit or a stuck contactor in condenser control circuit try these first then if not there in furnace control circuit at board that jockeys between air and heat remove thermostat wires from board remember thier location bet it stops.
Posted on May 13, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 08, 2016 | Heating & Cooling
If it is just the condenser fan that means you have a fan relay that has welded shut. Turn power off to your unit and trace the wires from your condenser fan back into the control panel at the unit. You'll have 3 wires going to it. 2 go to the run capacitor and one goes to the fan relay. The one that goes to the fan relay is the part that needs to be replaced. If you have no fan relay and it goes to the main contractor, half of your main contractor is welded shut and will need to be replaced.
Sep 18, 2014 | Carrier 52PQ-515---3 Premier Series Heat...
Dec 07, 2012 | Motorola Talkabout FR60 (14 Channels)...
Oct 16, 2010 | Samsung 18.8 Cu. Ft. Bottom-Mount...
Jul 09, 2010 | Goodman CLJ30AR32 Air Conditioner
Dec 04, 2009 | Refrigerators
Dec 01, 2009 | Napoleon 36" Zero Clearance Top/Rear Vent...
Oct 01, 2009 | Toshiba Satellite A215-S7422 Notebook
Jul 16, 2009 | Toshiba Satellite P35-S611 Notebook
Mar 26, 2009 | Heating & Cooling
98 people viewed this question
Usually answered in minutes!