Question about Heating & Cooling
Goodman Condensor cplj48-1 Air handler Modle AR61-1 Serial# 0206480558 7/8 Suction line and a 3/8 liquid line approx75'to 78' of line
Ambient temp 76
indoor temp 73
supply temp 66
Suction pressure 55
discharge pressure 155
this is a cap tube system
I notice grugling at Evaporator coil
My house is between 2700 and 2800 sq ft.
I think this is under sized but the system is not preforming
only a 6 to 7 degree temp drop
It sounds undercharged (needs more refrigerant). Based on the conditions in your post and assuming the indoor humidity is within 20-70% range, your target superheat should be 10degF. Your superheat (assuming you have an R22 system) is far too high. The pressures are not indicating a restriction; therefore, I have to conclude you have a low charge. A low charge will cause a gurgling sound due to the refrigerant in the liquid line is vaporizing prior to reaching the Cap tube at the Air Handler.
I hope you find this information helpful to you moving forward. :-)
Posted on May 10, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 20, 2014 | Goodman Heating & Cooling
Jun 07, 2014 | Goodman Manufacturing Goodman ARUF364216...
Aug 26, 2013 | Goodman CKL36AR36 Air Conditioner
Apr 12, 2013 | Bryant 462AJC021BA Air Conditioner
Feb 26, 2013 | Heating & Cooling
May 05, 2009 | Heating & Cooling
Oct 07, 2008 | Goodman Heating & Cooling
Sep 26, 2008 | Goodman Heating & Cooling
Aug 08, 2008 | Heating & Cooling
Oct 18, 2017 | Heating & Cooling
364 people viewed this question
Usually answered in minutes!