Question about Dayton (3E386) Heater
I have a dayton 30,000 btu heater ,,it will run for about 20 seconds and then shut off and then I have to push the reset button to start it again,,,,what could be the problem?
If you are pressing a small round switch with a tiny button in the center...means a bad heat exchanger. The heat from the exchangeris going where it is not supposed to and tripping a roll out switch. Have the exchanger checked for cracks or holes.....check vent pipe to make sure not plugged
Posted on May 10, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 04, 2015 | Heating & Cooling
Here are a couple of tips that I wrote that tell you how to troubleshoot a Torpedo or Reddy heater...
Reddy Heater - Troubleshooting Torpedo Heaters
Feb 03, 2011 | Dayton E48 Oil Filled Utility Heater
Jan 31, 2011 | All-Pro Kerosene Garage Shop Heaters - All...
Dec 28, 2010 | Dayton Electric Heater
Sep 17, 2010 | Dayton (2NH04502025) Heater
Mar 12, 2010 | Dayton Heating & Cooling
Feb 09, 2010 | Dayton (3E379) Heater
Jan 31, 2009 | Reddy Heater-170,000 BTU Kerosene Deluxe
Jan 17, 2008 | Procom QL300TYLA Heater
Jan 14, 2008 | Dayton E50 Heater
156 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: