Question about Weather King 12AJA4201AH Air Conditioner
I assume it is dripping water when the AC is running. If you look at the attic unit, there should be a PVC pipe running from the unit - probably an insulated PVC pipe. This pipe probably goes across the attic to the edge of the house and drains outside. The drain pan may also have a drain pipe, but the one on the AC unit is the issue, and is probably plugged. Go outside and see if you can locate the AC drain pipe. See if the ground is wet below the pipe and if water is steadily dripping from the pipe (with AC running). If the pipe and ground are dry, the pipe is plugged. If you have a wet/dry vac, try connecting it to the drain pipe outside to see if you can **** the pluggage out. If you can get it clear, water should start dripping out of the pipe. This same thing happened at our house. I decided to cut the pipe in the attic, and add in a PVC isolation valve, tee, and water hose connection with plug, so I can valve out the AC unit from the pipe, remove hose connection plug, and hook up a water hose and flush the line to outside. Lowe's sells all of the PVC pipe fittings. The water pressure from the hose will always flush out the algae and crud to the outside of the house. I can also remove the plug and pour a cup of bleach down the drain pipe every couple of months to keep algae growth in check. I also cut out the trap (u-leg) from pipe in the attic and purchased a ready made trap a Lowes (the contractor who built our house had made a lousy homemade trap). I purchased a few PVC elbows and installed the trap on the drain pipe outside. By the way, our AC drain pipe comes out of our wall outside and drains near our outside unit. Our secondary drain pan drain pipe comes out outside from an eave on the side of the house. I don't know what you drain line looks like (it may have a port to add bleach, or some cleanout provisions, maybe not). If you choose to modify/improve it, then make a sketch of it, go to Lowe's and get the PVC parts you need + PVC pipe primer and cement. PVC cement dries fast. Remember, the pipe must flow downhill from you AC attic unit. You can use a regular wood saw to cut the pipe. I hope this helps you. You need to keep the drain line clear as algae will continue to grow in it. Pouring bleach in the line every month or two helps. You also need to check maybe once a month that the line is draining properly (check to see if dripping outside). You can get some serious water damage to your ceilings if the water backs up and overflows. I discovered that our drain line was plugged just in time as our drain pan drain line was also partially plugged and drain pan was about to overflow.
Posted on May 08, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 12, 2014 | Heating & Cooling
Jun 27, 2011 | Heating & Cooling
Jun 19, 2011 | Heating & Cooling
Jun 05, 2011 | Carrier 38CKC060 Air Conditioner
May 01, 2011 | Goodman CKL36AR36 Air Conditioner
Jun 03, 2010 | Weather King 12AJA4201AH Air Conditioner
Sep 29, 2009 | Amana PTC153B35AJ Air Conditioner
Aug 03, 2009 | Coleman Heating & Cooling
Jun 21, 2009 | Weather King 10AJA3601AH Air Conditioner
Aug 09, 2008 | Heating & Cooling
485 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: