Question about Carrier XHB123D X/Y Series Heat/Cool Air Conditioner
Condenser is 10' above evaporator line set runs from condenser 16' down to get under house and back up 6' to coil with no trap other than the natural trap created by lineset. compressor starts ok gradually gets noisier until after about 30 min run time relief valve pops off until it goes out on thermal
Without putting gauges on the system... It sounds more like you either are overcharged, have a restriction in your system or your metering device is not operating correctly.. hope this helps
Posted on May 08, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
May 15, 2014 | Heating & Cooling
Oct 18, 2012 | Kelvinator Refrigerators
Apr 27, 2012 | Refrigerators
Jun 13, 2010 | Goodman CKL60AR60 Air Conditioner
Feb 04, 2010 | Electrolux ELD-726300 AOFP201RU Blast...
Aug 21, 2009 | Refrigerators
Aug 19, 2009 | GE (PSS26MSRSS) Side by Side Refrigerator
Aug 14, 2009 | Samsung AS1293L Air Conditioner
Jul 02, 2009 | Campbell Hausfeld Maxus 30 - Gallon Air...
Aug 01, 2008 | Ruud Matching Split Air Conditioner
66 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: