Question about Goodman CLQ36AR49 Air Conditioner
Unit comes on fan blades wont turn ... i have to bang the unit to make the blades come on
Can be a faulty motor start capacitor. Usually they will bulge if faulty.It is cheaper to replace that first, then if still the same fault look at replacing the motor
Posted on May 21, 2010
Sounds like the motor is tired. Time to replace motor...
Posted on May 06, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 07, 2014 | Fujitsu 12RLS Wall Ductless Air...
Aug 18, 2011 | Whynter Portable Air Conditioner
Jun 17, 2011 | Heating & Cooling
Mar 06, 2011 | Hunter Heating & Cooling
Aug 25, 2010 | Goodman CLT36AER36 Air Conditioner
Jul 11, 2010 | Heating & Cooling
Jan 02, 2010 | Ruud Central System Air Conditioner
Jun 06, 2009 | Goodman CKL42AR42 Air Conditioner
Oct 01, 2008 | Whirlpool Heating & Cooling
Sep 14, 2008 | LG BG8000ER Air Conditioner
179 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: