Question about Coleman Heating & Cooling
My heatpump's fan does not turn anymore. I was told it was the capacitor.Where is the capacitor located on a coleman heatpump and how to replace it.
If you're talking about the outside fan, look where the wire goes into the outside unit. The capacitor will be somewhere near the circuit board and will be round or oval and metal or plastic. If you're talking about the inside unit it will be with the electrical control in the air handler. Write down where the wires go. The terminals on the capacitor will be marked and for the outside unit you will either have 1 that runs both the fan and compressor or a seperate one for each. If you have 1 that runs both the wires must be reconnected to the right terminals. They will be marked COM, FAN, HERM(stands for compressor). Take the old one with you to get a new one. Let me know what you find.
Posted on May 04, 2010
Testimonial: "Thank you so much for your help. It makes me feel better ordering the piece now that you gave me the re-assurance. Tks again Antoinette "
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 26, 2015 | Coleman Heating & Cooling
Aug 31, 2011 | Coleman Mach 15 Air Conditioner
Jan 10, 2011 | Heating & Cooling
Jul 21, 2010 | Tools & Hardware - Others
Jul 08, 2010 | Coleman Mach 15 Air Conditioner
Dec 22, 2009 | Coleman Mach III Air Conditioner
Sep 09, 2009 | Coleman Mach III Air Conditioner
Jul 05, 2009 | Dometic 57915531 Air Conditioner
Jun 30, 2008 | Coleman Heating & Cooling
185 people viewed this question
Usually answered in minutes!