Question about Carrier 38CKC036 Air Conditioner
Only blower is working..will not shut off...no heat is generated...for awhile I could turn off power at fuse box and unit would provide heat for several cycles...but not now
I had the same problem and the result was an $82 limit switch just needed to be replaced.
Posted on Jan 06, 2009
Carrier products fall into a fail safe mode when any of the various overtemp sensors open or fail. check all of the micro switches that are around the burners and if any are open then that is your reason for the indoor fan to run nonstop. now you have to look at what caused the sensor to trip open. usually over heating. possibly a bad capacitor on the motor or the motor itself . or it could be excessive gas pressure creating to much flame and heat. test the gas pressure with a manometor. you can pick one up for about 100 bucks or call the gas company and see if they will come check it for free. then test the burners by observing flame pattern and flame rise off burners. then check the heat exchanger with a carbon monoxide detector . you can pick one up for about three hundred dollars . or try to get a gas guy that has one to check it. you may very well wind up calling a pro cause a simple mistake and you can easily kill some one or burn down the house. messing with gas aint the best way to save a buck. good luck.
Posted on Oct 15, 2008
1. check indoor wiring.
2 check selector switch.
3 heater not working.check heater eliment also.
Posted on Mar 28, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 27, 2015 | Pool & Spa
Jan 31, 2015 | Carrier WEATHERMAKER 48TCEA 4.0 ton Gas...
Nov 08, 2014 | Heating & Cooling
Aug 28, 2011 | Dewalt DG6000 Heavy Duty 6000 Watt Gas...
Feb 24, 2011 | Dayton Gas Furnace Heater
Feb 24, 2011 | Carrier Heating & Cooling
Jan 15, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Sep 02, 2009 | 1991 Ford Escort
Mar 17, 2009 | Goodman GMS90703BXA Heater
Jan 26, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jun 25, 2014 | Carrier 38CKC036 Air Conditioner
Jun 13, 2014 | Carrier 38CKC036 Air Conditioner
78 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: