Question about Raypak Free Hydraulic Lift Gate Delivery - No L...
Raypak b6000 boiler monitor control will call for heat when the b6000 boiler control is unhooked and not communicating to the boilers and how do you stop this call for heat.
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Raypak boiler nat gas for
Guessing you have a milivolt heater. While your pilot will light when you push the pilot light button down you need to generate 200mv to open the selenoid for the pilot and another 300mv for the main valve. This can be checked by removeing the leads from the pilot generator (wires from the pilot), Push the pilot button down and hold in place (a small screwdriver wedged in becide the button will do this) Then check the milivolt reading from the generator. This reading should be between 500 and 700mv (1/2 to 3/4 of a volt) If you don't have this your pilot generator is bad.
If you do then you need to hook the leads back up to the valve and unhook the saftey circut leads and try to light the pilot again. If the pilot still won't light your gas valve is bad. If it does then you have a problem in your saftey circut and you will need to check each item in the circut by removing and jumping past.
This would be more in line with just the main side of the valve not opening. So I'm sure you will find it to be the pilot generator or the valve being bad. As I stated before this system only runs on 1/2 a volt so all connections need to be clean and tight also. Could be other problems but this should cover the common reasons. Good luck.
Posted on Mar 13, 2010
Thank you for posting your question here on Fixya.com.
Replacing the roll out switch is an easy do-it-yourself repair. Fixing the problem causing the roll out of the burner flames in the first place is a bit more of a pro job. Something is causing to much heat to roll out the the combustion chamber into the control area causing the switch to fail. You will continue to burn the link until the underlying problem is fixed.
If this answer does not fix your problem, please comment with additional details prior to rating the answer. Positive feedback is appreciated once your problem is solved!
Posted on Jun 01, 2010
Tips for a great answer:
Jun 15, 2014 | Raypak Free Hydraulic Lift Gate Delivery -...
Feb 09, 2014 | Raypak Pool & Spa
Oct 05, 2012 | Raypak Pool & Spa
Mar 10, 2011 | Raypak Free Hydraulic Lift Gate Delivery -...
Dec 21, 2010 | Water Heaters
Sep 27, 2010 | Raypak Pool & Spa
Sep 21, 2010 | Raypak Free Hydraulic Lift Gate Delivery -...
Dec 30, 2009 | Rheem Paloma Tankless Water Heaters...
May 24, 2009 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
87 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: