Question about Ruud UBHC Air Conditioner
You said you have 120 vac but then you say you have it connected to the 240 v and common legs. If you have 120 v going to the transformer you should have it connected to the 120 v and common legs. Before you reconnect the transformer use an ohmmeter and check the secondary winding. It should be more than 1 and probably less than 75 ohms. Also check the primary winding you should get about the same range.
Posted on May 04, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 04, 2013 | Ruud UAKA037 Air Conditioner
Jul 26, 2011 | Ruud Matching Split Air Conditioner
Jun 22, 2011 | Ruud UBHC Air Conditioner
Mar 21, 2011 | Ruud Heating & Cooling
Sep 21, 2010 | Ruud UBHC Air Conditioner
Jul 05, 2009 | Ruud UBHC Air Conditioner
Apr 28, 2009 | Ruud Heating & Cooling
Oct 24, 2008 | Ruud UBHC Air Conditioner
May 28, 2008 | Ruud Matching Split Air Conditioner
81 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: