Question about Goodman CKL36AR36 Air Conditioner
I have goodman A/C unit model #CKL49-1, air is not blowing, the fans is not turning, when I turn the unit on, I hear it turn on but no air is blowing.
Your evaporator fan motor has quit. You need to find out if it is a relay or the fan motor. These systems come in various different setups. Updraft (vertical) or lay down (horizontal) you have to gain access to the motor and get it out. Turn off all power to the unit, look for any breakers at the panel. open the panel usually the same panel to access the filters. The motor and squirrel cage fan, will come out as one. look closely for rails at the top to slide the motor and cage out. Your wiring should unplug from the top close to the capacitor. you then can unbolt the motor - take pictures so you can reassemble it. Take the motor to a local HVAC store for a match. Be sure you get a new capacitor to go with the new motor.
Posted on May 04, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jul 26, 2012 | Goodman Heating & Cooling
Apr 23, 2011 | Goodman Heating & Cooling
Mar 31, 2010 | Goodman CLQ36AR49 Air Conditioner
Jun 13, 2009 | Goodman CKL42AR42 Air Conditioner
Jun 07, 2009 | Goodman CKL24AR24 Air Conditioner
Jun 04, 2009 | Goodman CLQ36AR49 Air Conditioner
May 26, 2009 | Goodman Heating & Cooling
Apr 25, 2009 | Goodman Heating & Cooling
Jun 25, 2008 | Goodman CLQ36AR49 Air Conditioner
880 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: