Question about Cooper Hammering
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
A switch is wired using the hot wires only, the black wire. It is simply a break in the line so that when the switch is off no power flows and when the switch is on the power does flow.
You are correct that the middle outlet would have two black wires and two white wires.
If you want to tap into that middle outlet and run power up the wall I suggest you look into some wiremold products. Go to their website, or any home depot and check it out. Get back if you think I can help you further. I am an electrician.
Here is a link that may help you.
Posted on Jun 02, 2009
This is a single pole light switch and should be wired as any other SP switch. The only difference is that is has a pilot light. All the white neutral wires are tied together and then pushed back in the box with none connected to the switch. The grounds are tied together with a jumper wire connected to the green screw on the switch. That will leave you with 2 or more black wires. If you have just two normally you can connect them to the two screws on the switch and it does not matter which screws. However it may be that with the pilot light you need to connect the wire going to the light to the top screw and the power wire to the bottom or vice versa. Try both ways. If you have more than 2 black wires you need to connect the incoming power black wire and outgoing power black wires together and then jump to one of the screws on the switch. The black wire left over is the black wire going to the light itself. If none of this works then it is obvious the pilot light in the switch is burnt out.
Posted on Jan 06, 2010
Testimonial: "Thanks a million. I will recheck the wiring tomorrow. Chas"
For this combo , the white wires connect to the two silver screws on one side of the combo .The black power wire connects to the screw next to the switch. IF you want to have the receptacle hot all the time then jumper the hot black from the switch screw to the receptacle screw. The screw in the center is for the black wire from any lihghts that you want to control. IF it is the receptacle that you wish to control with this switch .. then the power connects to the screw next to the switch and the center screw jump a wire to the screw next to the receptacle
Posted on May 04, 2010
Is the wire compatable for a 50 amp breaker. Also unit souuld be on its own dedicated curcuit, also how many amps is the service in the building, if your only at 100 amp it will not work.
Posted on Mar 06, 2011
SOURCE: I replaced my old 3way
Sounds as if you have a bad illuminated switch. The little LED or light inside the switch is itself possibly bad. Return it to the store and get a different one.
Posted on Jul 15, 2015
Tips for a great answer:
Aug 03, 2013 | Leviton 10 Brown Switch Outlet...
Oct 25, 2012 | Leviton Electrical Supplies
May 24, 2012 | Leviton Combo Switch Receptacle - 5225-T -...
Aug 27, 2011 | Leviton 5225WSP Switch and Outlet
Jun 17, 2011 | Leviton R01-7299-0NI Switch And GFCI...
Nov 13, 2010 | Leviton 5613-2WSP Grounded Switch
Nov 03, 2010 | Leviton Combo Switch Receptacle - 5225-T -...
Oct 25, 2009 | Leviton Combo Switch Receptacle - 5225-T -...
Jun 02, 2009 | Leviton 5225WSP Switch and Outlet
Apr 05, 2009 | Leviton 5225WSP Switch and Outlet
64 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: