Question about Briggs & Stratton Power Products 5,550 Watt Portable Generator #30241
Black max 7kw generator with 13 hp honda engine. While running in snow storm last winter quit producing voltage. Dried out and seemed to run ok and posered lights fine but i did not check voltage. Tried to run this week. Checked voltage and reads 145vac and 290vac. Hz is 62. opened the cover and conections looked good and clean, AVR looks to be hermetically sealed.
Those voltage readings MAY be normal.
The AC waveform may cause your meter to read inaccurately. You would need to use a TRUE RMS meter to accurately read the voltage.
The siple meters actually read the AVERAGE voltage and then are calibrated to mulltiply it by the "form factor" for a sine wave. OFTEN these generators don't produce a clean sine wave. A square-ish wave will read higher on the garden variety meters.
Compare the brightness of a lamp comparing to when run on your utility.
The frequency depends on engine speed ... yours is running a bit fast...check it under at least half load and if off, adjust the govenor slightly.
Posted on May 02, 2010
Testimonial: "Still working on the problem but tips were a real help."
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 13, 2014 | Coleman Powermate 7,000 Watt 13 Hp...
Dec 05, 2013 | Northstar North Star Honda 13hp 8000 Ppg...
The EU3000 series generators are inverter generators. The generator features an alternator, which produced high-voltage, multi-phase AC power. This power is converted to DC power and then converted back to AC. This process is controlled by a microprocessor and is necessary to provide stable, consistent power capable of running equipment sensitive to power surges. This type of generator provides higher fuel efficiency and lower operational noise ratings in a lighter model than home and work generators produced by Honda.
The Honda EU3000i Handi is a 3,000-watt inverter generator that features wheels, folding handle and a recessed convenience light. The engine is a Honda GX160, which features a 163-cc displacement. The AC output is 120 volts, with an average rating of 2,600 watts and a maximum production of 3,000 watts. There are three receptacles to include a 20A, 125-volt duplex and a 30A, 125-volt locking plug. The DC output is 12 volts and 100 watts. The EU3000i can hold 1.56 gallons of unleaded fuel, which will provide consumers with 3.6 hours of run time at 25 percent load for 7.7 hours.
May 31, 2012 | Honda Eu3000is
Oct 10, 2011 | Coleman Powermate Powermate 5000W...
May 16, 2011 | 2005 Honda Civic
Jul 27, 2009 | Electrical Supplies
Jun 10, 2009 | Northstar Generator 20 Hp, 13,000 Watt,...
Mar 31, 2009 | Coleman Powermate Premium Plus 6250W...
Dec 18, 2008 | Northstar Generator 13 Hp, 8000 Watt,...
Nov 28, 2008 | Electrical Supplies
1,624 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: