Question about Culligan Under Sink Water Filter
If this is a booster pump, many booster pumps like Shurflo have an adjustment at the top (allen screw) to back off on the pump pressure, turn to left to back off on pressure. If it never shuts off this can be an indication of a bad membrane, capillary tube, flow restrictor or automatic shutoff, causing all the water to run to drain. If you have low quantities of water, but pump always runs, this could part of the problem. Also high TDS (total dissolved solids) will cause the pump to work more. The higher the TDS 500+ppm the harder it is to produce quality water. With high TDS it's almost like taking muddy water, running it through filters and getting drinkable water. So the RO and pump have to work much harder to produce any quantity and quality of water.
Posted on Jun 03, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 16, 2015 | Refrigerators
on Apr 07, 2010 | Plumbing
Jan 21, 2013 | Refrigerators
Jul 17, 2010 | General Electric GE SmartWater Household...
Mar 03, 2010 | General Electric Profile Smartwater Ultra...
Jan 22, 2010 | General Electric Profile Smartwater Ultra...
Nov 04, 2009 | General Electric FX18M GE SmartWater...
Feb 21, 2009 | Home
229 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: