Question about Carrier Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Can you please check if the remote handset is this?
if yes, follow below
• Connect the system to the electrical current.
• Press the button M and of the remote control and keep them pressed down for at least
• The clock digits show the first configuration item (rAdr = remote address) and the temperature
digits show the default value of the respective configuration item (Ab = control of both indoor
• Press the button M repeatedly until "ASt " appears.
• Press the buttons ∧ or ∨ to change the default value (OF) to the new value (ON).
• Press the button to send the new configuration to the unit.
• Press the button to exit the configuration menu.
To see other available configuration options, consult the table.
Item Viewfinder display Explanation Description
1 1 "rAdr" "A": remote unit A Remote address of indoor unit A.
"b": remote unit B Remote address of indoor unit B.
"Ab": remote units A and B Default address of the two units.
2 "UCFG" "HP": Heatpump Default address and heatpump
"AC": Cooling only Changes the cooling-only address
3 "UAdr" 1-240 with an increment of 1 Address of the CNN unit.
Default = 1.
4 "ZONE" 1-240 with an increment of 1 Zone number.
Default = 0.
5 "GFdn" 1-240 with an increment of 1 GFD number.
Default = 1.
6 "A St" "OF" : Shutdown mode Select the function mode after an
"On" : Automatic restart electrical power failure.
If no button is pressed for 30 seconds, the remote control automatically exits the
configuration menu and the entire procedure must be restarted.
Posted on Apr 30, 2010
SOURCE: Identify unit capacity.
Carrier XHD183D 25" XH Series Heat/Cool Room Air Conditioner w/ 17800/17500 Cooling BTU, 230/208 Volts & 1870/1830 Cooling Watts.
The model you listed is what you have, Thanks, Sea Breeze
Posted on Jun 07, 2010
SOURCE: All our our Panasonic Split
The genset power most likely is 220V line to ground power. You utility power is 220V line to line but uses 2ea 110 VAC line inputs to get that 220VAC. The only way to correct this is to reconfigure your generator connection to 220V line to line IF possible. Some generators that only have a 220V output. Re-configuration is not possible
Measure power at the breaker on gen power as the source and again with the utility as the source. You will see the difference in voltages. Utility power.... each side of the Breaker output to ground = 110V across the 2 terminals 220V
Gen power one side of the breaker output = 220V other side = ZERO.
You can make it work but it would take some heavy duty relays in a power sub paenl so that when the generator is running one side of the power is 220V and the other side is Ground. Once utility power is restored the relays would disengage and power would again be 220 VAC line to line.
You will need a licensed electrician and a PERMIT to install a relay panel such as I mentioned above. Improper wiring of the power relay swtitching panel can cause major power problems in any given installation and trip the MAIN PWR breaker.
Thanks for choosing FixYa.
Posted on Sep 05, 2010
SOURCE: do i need to install
Before you buy, you have to calculate the heat load of your room and as well as the temp to be maintained in that room. Basing on that, there so many engineers in sales counter of every branded air conditioner to recomand you the correct model.And I hope with same expansion valve you can get required temp.
Posted on Dec 26, 2010
Tips for a great answer:
Aug 18, 2016 | Carrier Transicold Division Heat/cool...
Aug 12, 2014 | Carrier Heating & Cooling
Jul 02, 2014 | Carrier 36KCARMS Air Conditioner
Jan 01, 2013 | Heating & Cooling
Dec 25, 2010 | Heating & Cooling
Aug 19, 2010 | Carrier 38CKC036 Air Conditioner
May 27, 2010 | Carrier 38CKC036 Air Conditioner
Mar 18, 2010 | Carrier HEAT/COOL CEILING Air Conditioner
Jul 20, 2008 | Heating & Cooling
189 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: