Question about Sharp Heating & Cooling
Check the circuit breakers for the indoor fan. If you have power to the fan then you might have a bad capacitor or bad fan motor. Make the power is off and see if the fan rotates freely by hand. You can use a multimeter to check the capacitor and the fan motor. If it is not any of these you can look at the fan relay to see if it is working.
Posted on Apr 30, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 15, 2011 | Heating & Cooling
Jul 12, 2011 | Amcor AF9000E Portable Air Conditioner
Jan 03, 2011 | Heating & Cooling
Dec 04, 2010 | Heating & Cooling
Mar 24, 2010 | Heating & Cooling
Dec 13, 2009 | Air Purifiers
Nov 16, 2009 | GE Zoneline AZ38H12DAD Split System Air...
Aug 31, 2009 | Sharp Heating & Cooling
May 12, 2009 | Sharp Heating & Cooling
6 - DC Peak Error
• Supplied power is not normal
• Comp Connector (CN-U,V,W) is disconnected or inserted to wrong
• Compressor is damaged (coil short) ? replace compressor
• Too much Refrigerant
• Defect in outdoor pcb assembly ? replace pcb assembly
Try turning power off to external unit, usually resets diagnostics and runs OK. If not PCB external unit likely culprit, replace!
Jul 31, 2008 | Heating & Cooling
108 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: