Question about LG LS-L1210CL Mini Split Air Conditioner
HOW TO TEST A CAPACITOR
Posted on Sep 02, 2011
The compressor is probably tripping on high discharge pressure due to the slow fan rotation. That can be caused by a weak capacitor or the fan motor failing. The capacitor can be checked with a multimeter that has the capacitor check function. The capacitors are inexpensive but the fan motor will be another story. You should also check the voltage going to the fan motor.
Posted on Apr 29, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 24, 2016 | Inverter Heating & Cooling
Aug 10, 2010 | Goodman CLQ36AR49 Air Conditioner
Jun 18, 2010 | Goodman CLQ36AR49 Air Conditioner
Apr 10, 2010 | Goodman CKL24AR24 Air Conditioner
Nov 22, 2009 | Heating & Cooling
Aug 28, 2009 | Heating & Cooling
Jul 14, 2009 | Fujitsu 24R1 Air Conditioner
Jun 06, 2008 | Ruud UBHC Air Conditioner
Jan 04, 2008 | Heating & Cooling
429 people viewed this question
Usually answered in minutes!