Question about Water Heaters
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
is this a baxi 105? chances are you diaphragm has gone on your diverter valve. Or your diverter valve.
Do you will initially get a liitle hot water if your heating is on?
Posted on Dec 30, 2008
The first thing you need to do is to put some more water into your heating system. This is usually done by allowing water from your (pressurised) domestic cold water supply to flow into the system: On older boilers, this is done with a connection (often made with a removable hose) on the pipework just outside the boiler. Newer boilers may have a built-in connection with some sort of removable link (sometimes looks like a plastic key).
Once you've got the boiler up to working pressure (typically about 1 bar - 15 psi), you should be able to bleed your upstairs radiator properly.
This may be all it takes, though the pressure excursions you're getting when you run the hot tap suggest there may be another problem. See what happens to the pressure as the boiler heats up and cools down. There really ought to be very little pressure difference between the two conditions. If you see significant changes, this usually means that the "pressure vessel" (or in hydraulic terms, system accumulaor) has lost its air charge.
The pressure vessel is a metal container inside the boiler, usually painted in red enamel. Somewhere near the top, you will find a schrader valve (like the one on a car tyre), and you can use this along with a tyre pump to replenish the air in the top of the vessel. This will reduce your pressure transients for a while, but you need to keep an eye on it. If the problem returns, you probably need to replace the pressure vessel (or clag another one into the plumbing alongside the boiler).
Posted on Feb 03, 2009
Tips for a great answer:
Apr 10, 2015 | Water Heaters
Mar 02, 2017 | Water Heaters
Oct 27, 2009 | Protech Systems FasNSeal FSWMKE4 4" Vent...
Oct 12, 2009 | Water Heaters
May 06, 2009 | Water Heaters
Mar 23, 2009 | Water Heaters
Feb 03, 2009 | ACCO Brands Water Heaters
Oct 15, 2008 | Protech Systems FasNSeal FSWMKE4 4" Vent...
Aug 14, 2017 | Water Water Heaters
62 people viewed this question
Usually answered in minutes!