Question about Generac 100 Amp 120/240-Volt Transfer Switch #RTSN100A3
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The generators control board senses lost utility (N1 & N2) and after a time delay kicks in the backup. The board sends 12 v to the transfer relay thru wire 194 then back to terminal 23. This is held open till the startup timer times out and only after the warmup does wire 23 close to ground. This energizes the transfer relay, contacts close and E1 & E2 can now conduct generator produced electric to the transfer relay contacts, limit switch (XB1), Wire B, and a bridge rectifier.
Posted on Jan 24, 2010
Tips for a great answer:
Nov 28, 2016 | Office Equipment & Supplies
Feb 13, 2014 | Fisher and Paykel 23 in. DD-603SS Built-in...
May 21, 2012 | Kenmore Dryers
Aug 24, 2011 | Agri-Fab Agri - Fab Snow Blower - 42"
Sep 05, 2010 | Fisher and Paykel 23 in. DD-603SS Built-in...
Jul 29, 2010 | Fisher and Paykel 23 in. DD-603SS Built-in...
Dec 04, 2009 | Fisher and Paykel 23 in. DD-603SS Built-in...
Aug 07, 2009 | Texas Instruments TI-30XA Calculator
Feb 22, 2009 | Sony Handycam CCD-TRV318 Camcorder
Apr 19, 2008 | Nokia HS-23 Headset
70 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: