Question about Generac 100 Amp 120/240-Volt Transfer Switch #RTSN100A3

I assume 23 goes to 23 and 194 goes to 15b is this correct

Posted by on

• Level 1:

An expert who has achieved level 1.

New Friend:

An expert that has 1 follower.

Corporal:

An expert that hasĀ over 10 points.

Mayor:

An expert whose answer gotĀ voted for 2 times.

• Contributor

That is correct

Posted on Sep 21, 2012

Hi,
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Goodluck!

Posted on Jan 02, 2017

The generators control board senses lost utility (N1 & N2) and after a time delay kicks in the backup. The board sends 12 v to the transfer relay thru wire 194 then back to terminal 23. This is held open till the startup timer times out and only after the warmup does wire 23 close to ground. This energizes the transfer relay, contacts close and E1 & E2 can now conduct generator produced electric to the transfer relay contacts, limit switch (XB1), Wire B, and a bridge rectifier.

Posted on Jan 24, 2010

×

my-video-file.mp4

Complete. Click "Add" to insert your video.

×

Related Questions:

Scientific notation on BD - 107i calculator?

Of course it is possible!

There seem to be many ways to do this on this calculator.

Assuming we cannot do scientific notation, we can always do

6.02 x 10 ^ 23 / 3.01 x 10 ^23. However, we have to put brackets in to get BEDMAS to work correctly!

6.02 x 10^23 / (3.01 x 10^23) - for the 10^23, type 10 then the y to the x key and then 23.

Using the scientific notation, we can type in 6.02 EXP 23 / 3.01 EXP 23.

Good luck with your chemistry test tomorrow!

Take care,

Paul

Nov 28, 2016 | Office Equipment & Supplies

Fisher paykel dishdrawer lid will not stay locked

Assuming this is happens with only one drawer - most likely controller is recongising some sensor problems. If the water inlet is faulty then it is waiting for water to get in. Alternatively, the sensor that tells it the drawer is closed suddenly misbehaves and confuses the controller which stops the cycle.

Feb 13, 2014 | Fisher and Paykel 23 in. DD-603SS Built-in...

Bottom draw used infrequently - coonot use comes up with code LP

I am assuming the top drawer is working ok.

The code LP (meaning low pressure) is possibly linked to the inlet water not coming in at the correct pressure.

If this is happening with the bottom drawer only, then the likely cause is a kink or cracked inlet water connection to the drawer. YOU will have to turn the power and water connection off and pull the drawer out to inspect.

Sep 05, 2010 | Fisher and Paykel 23 in. DD-603SS Built-in...

Had a power cut today,top draw does not power up

I am assuming you lost power to the house while the dishwasher was running. The power is back but ou are not able to start the top drawer. Is that correct?

Was the top drawer operating at the time the power went off? Are you able to pull the drawer out?
Do any lights turn on when you press the Start button?

Jul 29, 2010 | Fisher and Paykel 23 in. DD-603SS Built-in...

Soap doesn't empty from dispenser

Assuming you are using the correct detergent powder, check if the dishes are remaining dirty.

The water from the impeller may not be rushing up enough due to blockage or limited movement of impeller arm. Follow the insructions to clean the impeller, filter etc or check base of drawer for obstructions to impeller arm.

Dec 04, 2009 | Fisher and Paykel 23 in. DD-603SS Built-in...

Entering 6.02 X 10^23/ 206 =

I think I'm reading this correctly. In your exponent, you are dividing 23 by 206. If so, enter in the calculator the following way:

6.02 x 10 ^(23/206) and then the enter/= key. You should get an answer of 8. The ^ key is 4 keys above the "on" key. You must use parentheses around the fractional exponenet

Aug 07, 2009 | Texas Instruments TI-30XA Calculator

Code C:31:23 quikly flashing over a underlined triangle...HELP!

Error C:31:23 problem means that System Control is not getting Supply Reel pulse. This can be electronic or mechanical problem in camcorder.

Qualified camera tech will fix it properly.

Feb 22, 2009 | Sony Handycam CCD-TRV318 Camcorder

HS-23 problem disconnected

Assuming that the joint which connects the neck strap has been damaged ( see below image )

, I advice you fix the loosed or broken joint back in its proper place permanently by using fevi kwik or some other fast bonding adhesive, but the only problem which will remain is that each time you have to use the headset you will have to wear it through your head andremove it the same way.

Apr 19, 2008 | Nokia HS-23 Headset

Open Questions:

Related Topics:

70 people viewed this question

Usually answered in minutes!

Level 2 Expert

Level 2 Expert