Question about Heating & Cooling
I have a brivis MPS Gas Ducted Heater,but today wall control is not display,please help!!!
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
When it comes to error 62 resetting the unit probably won't work. Because the NG1/lo is INSIDE the heater it is subject to significant hot / cold temperature fluctuations - causing crystallisation in soldered joints on the PC board and a loss of electrical continuity.
Posted on May 05, 2010
Error 62 is related to hot surface ignitor (HSI)or/nglo module
you can check the resistance of the ignitor should be less than 10 oms @ 20 degrees
failing that, if you incomming suppy exceeds 270 volt will also result in error 62
Posted on May 15, 2010
Testimonial: "The error did indicate an HSI problem but it turned out to be a fault on the circuit board of the control module, thanks anyway"
test thermosat for proper operation ie-broken wire-power if good jump stat and check if unit goes on if it does than stat internal problem or wiring problem and needs replacement or repair --if stat good check fan safety/high limit sensor if good would need to check and test thermocouple thats the tube that the pilot flame burns on may be enough to keep pilot burning but not enough to open valve for heat demand
Posted on May 31, 2010
Tips for a great answer:
Apr 20, 2014 | Heating & Cooling
Jul 26, 2013 | Cars & Trucks
Apr 25, 2013 | Heating & Cooling
May 31, 2010 | Heating & Cooling
May 04, 2010 | Heating & Cooling
Apr 30, 2010 | Heating & Cooling
Apr 12, 2010 | Heating & Cooling
May 12, 2009 | Heating & Cooling
Jun 10, 2008 | Heating & Cooling
319 people viewed this question
Usually answered in minutes!