Question about Heating & Cooling
Hi. I have a Rinnai Timberflame Centrum gas fire. It is constantly cutting out with the number 12 flashing in the screen. I can not find my manual nor can I find one online. Could you please tell me what code 12 means and if possible where I can get a manual online. Many thanks, Tracy
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: my rinnai gas log fire
Fault code 12 means the flame lit ok but hen for some reason went out. In my experience this usually means a fault on the gas supply itself. If you are on lpg I have had many problems with gas regulators recently. If you have something else on gas like a cooktop, fire that up first, then try the log fire. If this seems to fix the fault get a gas fitter to change the regulator.
Make sure all taps and isolattion valves are fully on.
I'm have assumed this is not a new installation so the unit has worked ok before.
Does the flame stay strong after it lights. If it slowly fades then definately a gas supply problem.
If it stays strong but just shuts of with a click, then possibly a fault on the heater, check the rod the flame heats is well in the flame. Could be the electronic otherwise but very rare.
If the flame goes yellow like a candle and then shuts off you will need to check the flue or chimmney as this might be blocked..
Cheers, let me know if anything works and re-post with any more info if you are still stuck, I will keep a look out for you.
Posted on Aug 09, 2010
I had this same problem last year and went through all the checklist in poshpoms suggestions ( I am on mains Gas ). The issue was caused by the Flame rods. Near the 2 pilots at the front and the back. Those small rods each that 'senses' the flame become inadequate, so they were replaced with a new pilot assembly from Rinnai that had longer rods and better coverage. Issue was fixed. Good Luck.
Posted on Sep 09, 2010
Tips for a great answer:
May 17, 2011 | Rinnai Heating & Cooling
Sep 06, 2010 | Heating & Cooling
Aug 23, 2010 | Heating & Cooling
Aug 08, 2010 | Heating & Cooling
May 13, 2010 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Jul 29, 2009 | Rinnai EnergySaver 556 Air Conditioner
Dec 31, 2008 | Rinnai Webstone The isolator EXP tankless...
Mar 20, 2017 | Rinnai Vent Free Gas Heater/: 6,000 BTU...
Aug 19, 2017 | Frigidaire Heating & Cooling
379 people viewed this question
Usually answered in minutes!