Question about Hayward H Series Induced Draft Abg 100,000 Heater
Gas lights and turns off 10 seconds then 30 seconds later it relights then goes off again continously; water is circulating heater fan is on gas on and electric on i tested temp control and that is working >
Assuming you don't hear any banging noises, that cycle is by design. There is a fault. 2 possible causes are the ignition board is bad, or the ignition sensor is not returning a voltage indicating the flame is lit. Take this out and put the ignition piece on your stove flame. Check for voltage while on flame (DC millivolt setting on multimeter). Put one probe on ground other on sensor lead. If it doesnt have voltage this is bad. If you do, its possible your board is bad.
Posted on May 24, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 20, 2014 | Hayward H-series Electronic Gas Pool...
Jun 08, 2013 | Pool & Spa
May 12, 2013 | Pool & Spa
Nov 29, 2012 | Watches
Jan 21, 2011 | Raypak 2100 Pool Heater Gas 266000 BTU'...
Jan 04, 2011 | Reliance WATER HEATER CO #1-30-YOPT-D...
Nov 14, 2009 | Reddy Heater-75-125,000 BTU Variable
Jan 17, 2009 | Pentair Mastertemp Pool & Spa Heater Dual...
Aug 01, 2013 | Hayward H Series Induced Draft Abg 100,000...
1,297 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: