Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Try to replace the thermostat. Short cycling of motor only happens when the thermostat is set to a very high temperature.
Posted on May 27, 2009
I think the wiring diagram is on a printed sticker on the side of the water collector, just pull it out of the right side as you look at it. There should be one on there hope this helps as i have the same unit in the other room. regards Richard
Posted on May 29, 2009
is the pump youll have to take off a panel make sure the pump has water. what is the relative humidity if it is high swampers don't work very well .Tom
Posted on Jun 26, 2009
Evaporative coolers are only for dry climate
conditions or deserts. They cannot cool
as much as central air or air conditioners which have compressors and refrigerant. The mechanics are simple requiring a water
float valve, pump, spider (water distribution), aspen wood pads, blower, belt,
motor, and switch. The unit must have a water
supply to replenish the system due to evaporation. Your system may have a float
valve which you need to adjust to shut off when the water pan is full. Floats
can be adjusted by loosening the pivot screw and moving the float up and down
to adjust the turn off level or by turning the float to extend or retract the
length changing the water shutoff position. You do not want the water to be so
high it flows out the over flow tube but the water should cover pump base. Plug
in the unit and turn the switch to pump if you have that option on your
unit. This will engage the pump to force water from the pan up to the spider to
saturate the pads with water. After a few minutes turn the switch from pump to
low or high cool. New aspen pads will have an distinct smell which will go away
after a few days of usage. If you do not have a pump setting turn the switch to
low or high cool which will blow warm air at first then start to cool down. You
may also have a fan setting which will blow outside air without any additional
cooling if the outside air is humid. Occasional maintenance is to make sure the
pump is pumping water and the filter basket is clean and all the spiders are
working with water flowing freely. You can use a flexible wire to force it in a
spider tube to clean it if it is clogged. You may want to change the water
after a month to keep the system cleaner from slime and calcium. At the end of
the season disconnect the water supply and drain the water pan blowing out the
water line if the winter is below freezing. Replace the pads if they have
calcium build up or dry. Flush the water pan out and clean the Add some oil to the pillow blocks which are
the bearings at each end for the blower. Check the belt and pulley for
excessive wear. Cover the unit with canvas to prevent cold air from coming in
during the winter. Next summer season all you have to do is uncover the unit
and hook up the water supply.
Posted on Jul 27, 2010
Tips for a great answer:
May 31, 2014 | AdobeAir Mobile Swamp Evaporative Air...
Apr 16, 2012 | Mastercool 67680 Evaporative Cooler Air...
Jun 15, 2011 | AdobeAir Mobile Swamp Evaporative Air...
Jun 14, 2011 | Heating & Cooling
Apr 24, 2011 | Mastercool 67680 Evaporative Cooler Air...
Jul 20, 2010 | Mastercool Portable Air Conditioner
May 04, 2010 | Cfm Kenstar Turbocool Major Portable Swamp...
Apr 12, 2010 | Cfm Kenstar Turbocool Major Portable Swamp...
509 people viewed this question
Usually answered in minutes!