Question about Rheem RTG-53XP Outdoor Liquid Propane Tankless Water Heater for 1-2 Bathroo
I have power to unit, I push "SW1" button inside ; the fan does start !!
Gas valve is open and have 200+gal of propane in tank !!
Unit is only in use 15 months
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Turn the gas knob up. There's a dial on the front (probably red) and it will have settings on it. A B and C. Turn up to desired temp, but be careful of faucets if there are children in the house. Good luck
Posted on Jan 05, 2010
if your on a private well, it sounds as though your loosing enough water pressure to shut the heater off,.(which is right before the water pump comes on),....tankless heaters turn on by sensing water flow, and of course off when flo stops,......water pressure tanks often need to be re-charged with air for pressure to stay even,....does your water pressure fluctuate?
Posted on Jan 10, 2010
Tips for a great answer:
Apr 03, 2013 | Honeywell Water Heaters
Oct 25, 2012 | RELIANCE ELECTRIC WATER HEATER
PROBLEM #1 - HOT SURFACE IGNITOR DOES NOT GLOW RED
(Remember to wait for purge time, 17/34 seconds, on models so equipped).
A. No main power
B. Faulty transformer
C. Faulty thermostat
D. Faulty limit switch
E. Faulty blower interlock switch
F. Faulty hot surface ignitor
G. Faulty ignition control
Perform normal system checks of main power, transformer, thermostat, limit
switch, blower interlock switch, and replace faulty component.
With power on and thermostat set at its highest position, check voltage
between "TH" and "TR" on HS780 ignition control. If 24 volts is not present
check output at transformer. If no, replace transformer. If transformer
checks out OK look at other controls in the 24 volt circuit I.E.: thermostat,
limit switch, blower interlock switch. Check for 120 volts between "neut"
(L2) and "120" (L1). Check for 120 volts at the ignitor across "IGN" and
"IGN" terminals on the HS780 ignition module. If 120 volts is present,
replace ignitor. If no, replace the 780 series module
PROBLEM #2 - IGNITOR GLOWS RED BUT MAIN BURNER
A. Improper ignitor alignment
B. Faulty ignition control
C. Faulty gas valve
D. High inlet gas pressure
E. Polarity reversed
F. No earth ground
Check for availability of gas at gas valve. Make sure the manual valve
upstream of the gas valve and the gas valve are in the full on position. Also
make sure gas is being supplied to the system at the proper pressure, too
high will lock-up the valve.
Check proper polarity of "NEUT" and "120" on the ignition control by reversing
the wires, if reversed gas valve will not open. If this does not solve the
problem, replace wires as they were.
Check for proper ignitor position.
Check for a good earth ground by using a meter connected between L1
and furnace chassis. Should read 120 volts, if no, check and/or repair ignition
ground wire or ignition control mounting screws.
CAUTION POLARITY MUST BE OBSERVED
Check for 24 volts at the gas valve terminals; "1" and "2" on a 7200 series,
"M" and "C" on a 7100 series, "TH" and "TR" on a 7000 series. If yes,
check wire integrity or change the gas valve. If no, change the 780 series
That is pretty much all of the troubleshooting required.
Thanks for choosing FixYa,
Feb 14, 2011 | Rheem 40 Gallon FVR NATGAS Low WATER...
Dec 22, 2010 | Rheem 50 Gallon FVR NATGAS Water Heater...
Jul 12, 2009 | Rheem Tankless Hot Water Heater...
Jul 08, 2009 | Water Heaters
May 30, 2009 | Water Heaters
May 18, 2009 | Water Heaters
Apr 08, 2009 | American Standard Water Heaters
Mar 16, 2009 | Water Heaters
36 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: