Question about Intermatic T101 - 24 Hr. Dial Time Switch - NEMA 1 Indoor Steel Case - Gray
If the timer is already installed, then the incoming (from the breaker or source) black wire should be connected to the #1 terminal. The incoming white wire should be connected to the "A" terminal and the bare (or green) wire should be connected to the "GR" screw on the (lower) case.
To connect the pool filter (load) to the timer, connect the black wire to terminal #2, the white wire to terminal "A" (along with the incoming white wire) and the green wire to the "GR" screw (along with the incoming bare or green wire). Usually one twists the two green or bare wires together with a short pigtail using a yellow or red wire nut and then connects the pigtail to the "GR" screw.
The two white wires don't need to be pigtailed, as the "A" terminal is designed for two wires.
Posted on Apr 25, 2010
Testimonial: "Thanks for your help. I am going outside to give it a try and I'll let you know how it goes. Hopefully I won't shock myself again. Thanks Again!"
Just put the wires together like its wired now. Put the black wire underneath the same screw as the black wire on the LOAD side. Then, the white and green go underneath the same screw as the other white and green.
Posted on Jul 10, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 19, 2014 | Woods In-Wall Digital 5-10-15-30-Minute...
Aug 11, 2014 | Hardware & Accessories
Aug 21, 2012 | Intermatic T101P3 Pool Timer IndoorOutdoor...
Jul 06, 2011 | Paragon 4001-00 24-hr Timer Control 120v...
Apr 17, 2011 | Intermatic & Self-Adjusting Wall Switch...
Sep 21, 2010 | Intermatic & Indoor/Outdoor Rain Tight...
Jun 04, 2010 | Intermatic EI210 Electronic Auto Shutoff...
Oct 03, 2009 | Intermatic & Indoor/Outdoor Rain Tight...
Aug 22, 2009 | Intermatic T101 - 24 Hr. Dial Time Switch...
372 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: