Question about Heating & Cooling
I have an Armstrong Air furnace that is not blowing hot air. Noticed the LED light is flashing four times, which, according to the alarm code means I have a high limit switch open. Turned the furnace off and back on but that didn't do any good. How do I find and manually close/reset the high limit switch??? Thanks!
If you know where the high limit switch is you can always cut the two wires and wire them together causing the limit to close. But what you have to watch out for is why the high limit is not closing. That means in your return air either you have a dirty return air duct, dirty filter, or you don't have all your registors open to allow the heat to escape the heat exchanger. Just watch over riding the system. The high limit switch should either be on or behind the blower, in the middle of the system right under the heat exchanger. any other questions about hvac just ask.
Posted on Jan 17, 2009
You need an ohmmeter. Start checking all thermal limit switches
and fuses. Remove one wire when checking and also turn voltage off to unit. It could be a resetable switch, start pressing all the pop up buttons on the switches.
The cause could be simply - dirty air filter or a blower assy problem, or dirty flue vent, or induce draft fan problem.
Posted on Mar 23, 2008
I have an Armstrong high efficiency 90+ Condensing Gas Furnace. The Blower works on Cool, but not when the Heat is on. The LED flashes 3 times: Fault is Pressure Switch open with inducer on"
Where is the combustion blower? Is this an easy fix?
Posted on May 12, 2010
The limit switch is one of several built-in safeties designed to protect the furnace and prevent a possible explosion. Rule # 1, i.e. don't put jumpers or do any other things that you don't fully understand as it is extremely dangerous to play with furnaces. Remember, you are not a certified HVAC mechanic. Rule # 2, i.e. read the manual and follow simple steps such as find any blockages, open closed registers, etc. Rule # 3, i.e. if all the above doesn't help, don't be a frigging idiot and call a professional !!!!!
Posted on Dec 29, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 19, 2015 | Armstrong Lennox Ducane Armstrong Gas...
Oct 06, 2012 | Honeywell Furnace Air Pressure Switch...
Mar 22, 2011 | Heating & Cooling
Dec 26, 2010 | Goodman CACF048B2A Air Conditioner
Jan 10, 2010 | Armstrong H 67 1PH Bf In Line Circulator...
Jan 10, 2010 | Heating & Cooling
Dec 09, 2009 | Heating & Cooling
Dec 31, 2008 | Heating & Cooling
Nov 23, 2008 | Heating & Cooling
8,631 people viewed this question
Usually answered in minutes!