Question about APC Heating & Cooling
SHOULD HAVE 4 LUGS 2 LABELED LINE AND 2 LABELED LOAD. THE 2 LINE IS 230 FROM BREAKER THE 2 LOAD IS 230 TO CONDENSER. SHOULD HAVE 2 GREEN GROUND WIRES THAT MOUNT TO HOUSING.
Posted on Apr 24, 2010
Testimonial: "That was very helpfull, I wasn't sure where to attach leads from main breaker- you've answered my question, thank you much Al. "
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 06, 2017 | Electrical Supplies
Sep 22, 2013 | Cutler Hammer Electrical Supplies
Dec 11, 2010 | Cutler Hammer 100 Amp Main Breaker...
Aug 09, 2010 | Cutler Hammer Fusible AC Disconnect Switch...
Jul 27, 2010 | Cutler Hammer Eaton Electical #BD3030...
Jun 18, 2010 | Cutler Hammer Eaton Electical #BD3030...
Mar 22, 2010 | Heating & Cooling
Jan 07, 2010 | Cutler Hammer Fusible AC Disconnect Switch...
Sep 15, 2009 | Cutler Hammer Eaton Electical #BD3030...
Sep 04, 2009 | Cutler Hammer Eaton Electical #BD3030...
455 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: