Question about Computers & Internet
This is not a PC problem
Heating comes on, but sometimes it
gets too hot, sometimes too cold.
Neutral not connected
Check wiring in room thermostat. Look for a
connection to the Neutral terminal (N 2 on
the Honeywell T6060, T6160, and T6360).
Make sure that it is connected (check
If there is no neutral available, replace with a
two-wire thermostat, e.g., CT200, CM61 or
CM67. These will also offer extra energy
savings, (Without a neutral connection, the anticipator within the room thermostat does not work,
so the temperature control reduces from ± ½ºC to ±3ºC. People can feel a six degree
temperature swing. Then, if they try to adjust the room thermostat to overcome the
problem, the temperature swings become even worse.)
Posted on Mar 16, 2008
a 6ya Technician can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Technician (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 10, 2015 | Honeywell Programmable Thermostat Heater
Feb 15, 2015 | Honeywell RTH221B1000-OB Open Box Basic...
Dec 11, 2013 | Honeywell Programmable Thermostat Heater
Jan 29, 2011 | Honeywell Heating & Cooling
Jan 19, 2010 | Honeywell Electronic Programmable...
Nov 30, 2009 | Honeywell Programmable Thermostat Heater
Jun 17, 2009 | Honeywell Focus 6300B 5-2 Days...
Jan 25, 2009 | Honeywell Focus 6300B 5-2 Days...
Oct 23, 2008 | Honeywell Programmable Thermostat Heater
517 people viewed this question
Usually answered in minutes!