Question about Heating & Cooling
The outside unit is tripping the reset button.
Once the unit is reset the unit runs fine.
Could this be a outside fan issue?
Maybe a bad spot on the motor causing a heavy load on startup.
When the outside unit is tripped the inside unit continues to run with no heat and the backup heat does not start?
You may be right in looking at the motor. It uses a different speed on heat than cool. The heat cycle uses low speed, usually red. Some manufactures use blue (medium). Cool uses black, high speed. If you are confident, switch the low speed wire with the high speed and see if this changes anything. If the fan motor isn't the problem, check the other setting (cool) if the overload trips, you may need to look into a new capacitor or compressor, if so, you can install a hard start kit. these are start boosters, and are inexpensice, sometimes they will give another year out of the comp. but I've put them on and they have lasted 5 years.
Posted on Mar 15, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 06, 2011 | Ruud UBHC Air Conditioner
Dec 10, 2010 | Heating & Cooling
Dec 09, 2010 | Ruud Central System Air Conditioner
Aug 08, 2010 | Ruud UBHC Air Conditioner
Jan 02, 2010 | Ruud UBHC Air Conditioner
May 11, 2009 | Ruud UBHC Air Conditioner
Apr 24, 2009 | Ruud Central System Air Conditioner
Oct 23, 2008 | Ruud Heating & Cooling
Nov 20, 2007 | Ruud Central System Air Conditioner
412 people viewed this question
Usually answered in minutes!