Question about Dishwashers
I had the same errror code on my coleman furnace (3 flashes combustion air switch failed to close) but at first didnt realize there was even a light that gave codes..Anyways long story short, after searching many forums one guy mentioned about the furnace giving a false reading and talked about improper air flow ( coming in and going out) which isnt triggering the switch correctly. After thinking about it and after getting the furnace to run correctly every time I took the door off to tap on the switch (and other spots not knowing what the problem was yet) I always put the door right back on then the furnace would do the same thing (stop running). so I pulled the door off again got the furnace to work properly and left the door off and tested it. It ran great, it started and stopped like normal for a hour and realized I might not be getting proper air flow. Then I remembered I asked my roommate to change my filters for me while I was gone (which he did) and looked at them while I still had the door off and realized the filters were in backwards! which resticted the air flow so much the switch wouldnt operate fully. so check your air filters, something so stupid almost cost me a house visit by the furnace guy....this may not be everyones problem but maybe I will help someone save a house visit....I still cant believe that was my problem and the furnace is still running great.
Posted on Dec 01, 2009
I followed the instructions on the furnace to reset the ignition switch to off...turn off all electrical power to the furnace...wait 10 minutes...turn on all electrical power & the ignition switch to on...didn't work the first time so I followed the same procedure except this time I also reset the circuit breaker (which was fine anyway) & this time it worked...
Posted on Nov 30, 2008
My furnace buzzes but dont come on
Posted on Sep 30, 2011
Did you check the air switch hoses. Sometimes debris gets in the line and causes the switch to stick.
Posted on Apr 22, 2008
I have been having the same problem with the same model for the last 3 years. It doesn't seem like any professional I have called has a clue of how to fix it because everytime I call someone they come out and replace something and then within a couple months the same thing happens again.
Posted on Oct 13, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 14, 2014 | Coleman 7990-319p Evcon Gas Furnace...
Dec 22, 2012 | Coleman Mobile Modular Home Gas Furnace...
May 09, 2012 | Coleman Propane Forced Air Heater...
Sep 21, 2011 | Coleman Heating & Cooling
May 11, 2009 | Heating & Cooling
Jan 20, 2009 | Coleman Propane Forced Air Heater...
Oct 02, 2008 | Heating & Cooling
4,908 people viewed this question
Usually answered in minutes!