Question about Powerware 9120 UPS System
Hi - Where exactly is the IRF630fet - I am also going to try to replace the 2 Capacitors - if I can find them! - You mentioned the 100uf/63v and 2200uf/16v capacitors - Cheers - Terry
Normally DC BUS FAULT is fixed by replacing C14 and C10. C14 is the 100uf/63V and C10 is 2200uf/16V. They are located between the heat dissipator and the logic board near transformer TX1.
Posted on Mar 12, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 04, 2015 | Powerware 9120 UPS System
Nov 13, 2013 | APC Smart-UPS RT 3000VA UPS System
Nov 13, 2013 | APC Computers & Internet
Jan 27, 2011 | Powerware Ferrups 3.1kVA L5-30P (3) 5-15...
Oct 12, 2010 | APC - UPS - Matix/Symmetra Enterprise UPS...
Sep 15, 2010 | MGE Galaxy 3000 UPS System
Nov 13, 2009 | APC - UPS - Matix/Symmetra Enterprise UPS...
Mar 16, 2009 | Exide Chloride Power Station (EXP2000) UPS...
507 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: