Question about GE GSH25KGRWW Side by Side Refrigerator
How do i troubleshoot the relay and the overload on the compressor?
The relay will be burnt up inside, shake it and little pieces will come out if its burnt out. the overload usually is never the problem
Posted on Mar 12, 2008
I am told if you measure two terminals and note the two with the highest resistance. Then measure each of the two terminals with the highest resistance to the common terminal they the two additional readings should read the same as the two terminals with the highest resistance when adding them together. If after adding the two there is more than 1/2 ohm difference one of the windings is shorted.
Posted on May 06, 2009
if your taaalkking about a three in one the instructions are on the relay. to determine where the wires go on the compressor google the model number or the maker of the compressor then find the correct connections to make on the compressor also make sure that the replacement relay is iin the correct position.
Posted on Feb 06, 2009
HI. i would recommend to check the relay first, then the compressor last to confirm total failure. If both devices test out ok, this will lead to a failed main power control board.
The compressor relay starts the compressor. A fault relay can result in the compressor failing to cycle on. The relay is accessed from the lower rear of the refrigerator. The compressor relay can be accessed by removing the terminal cover box. The cover is held on by tension or with a retaining clip. On some units. the relay may not be covered at all.(each model may vary). Beneath the terminal cover(if equipped), you will find the compressor relay, and the overload protector as well. The electrical terminals of the compressor motor are located here also. Remove the compressor relay by pulling it straight off from the compressor, gently. Pull the wire off of the side terminal of the relay. It is connected with a slip on connector. Firmly pull the connector, do not pull on the wire. You may need to use a pair of needle-nose pliers. Inspect the connector and terminal for corrosion. If either is corroded they should be cleaned or replaced. There are two types of relays you may encounter, wire coil and solid state. If the relay has an exposed wound wire coil it can be tested for continuity. Otherwise, the relay is of solid state design and requires specialized equipment for testing. Test the relay with a ohm(multimeter), for continuity. Set the meter to the ohms setting X1. With the relay upside down, place the probes into the terminals labeled "S" and "M"(the labeling may vary on each model). The meter should display a reading of zero ohms, indicating continuity (or if using a continuity tester, it should light up). With the probes still in place, turn the relay over. You should hear the click of the magnetic switch engaging. The meter should now display an ohm reading of infinity (or the tester should not light up). Turn the relay upside down again, place the probe on the "S" terminal and place it on the side terminal labeled "L". The meter should now display a reading of zero ohms (continuity). Turn the relay over and the reading should change to infinity. With the relay upside down place one probe on the "L" terminal and the other probe on terminal labeled "M". The meter should display a reading of zero ohms. Turn the relay over and the reading will stay the same, zero ohms. Now, if the relay fails these described tests, it should be replaced asap.
COMPRESSOR TEST PROCEDURE
The compressor is accessed from the lower rear of the refrigerator. Generally the same proximity of the relay. The compressor motor can be accessed by removing the terminal cover box. The cover is held on by tension or with a retaining clip. The main testing points will be the actual terminal post that hold the relay, gently pull the relay of the terminal box on the side of the compressor, and use the relay holding probes for testing. Once the relay is removed, Place one probe on any terminal and then touch the other probe to each of the other two terminals. The multimeter should display a reading of zero ohms. Be sure to set your meter to 1X before beginning. Now move the first probe to a different terminal and test the other two terminals with the other probe. Finally, move the first probe to the last terminal and test each of the other terminals with the other probe. Every test should have continuity with the multimeter displaying zero ohms. If the compressor motor does not pass all of these tests, the compressor will require professional service. Now test the compressor for ground. With the multimeter still set to X1, touch one probe to bare metal on the compressor housing (it may be necessary to scratch away a little paint to expose the metal). Touch the other probe to each of the three terminals in turn. None of the terminals should have continuity; the multimeter should display a reading of infinity. If any of the grounding tests show continuity, the compressor will require professional service.
Posted on Jan 10, 2010
are you sure the condenser fan is running correctly to move air over the condenser and is the condenser free of dust and dirt so it can cool properly from air movement from the fan
Posted on Mar 23, 2010
Tips for a great answer:
Apr 22, 2016 | Refrigerators
on Apr 04, 2011 | Refrigerators
Aug 19, 2015 | Refrigerators
Nov 27, 2012 | Refrigerators
Sep 21, 2011 | Refrigerators
Sep 05, 2011 | Refrigerators
Dec 10, 2009 | Jenn-Air Refrigerators
Nov 18, 2008 | Maytag PSD2450G Side by Side Refrigerator
Apr 04, 2008 | Refrigerators
Dec 29, 2010 | GE GSH25KGRWW Side by Side Refrigerator
553 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: