Question about Air Conditioners
Is the contactor engaging? Make sure it is getting 24v. If not, check the low pressure safety, outside thermostat (if you have one) and the defrost board. Follow the low voltage from the thermostat to all these controls, up to the contactor. Check the thermostat too. If you need a walk through I can help, if you have a volt/ohm meter.
Posted on Mar 02, 2008
Tips for a great answer:
Jun 07, 2016 | Intertherm Air Conditioners
Sep 11, 2013 | Intertherm Air Conditioners
Nov 02, 2011 | Intertherm P3RA-048K Air Conditioner
Dec 03, 2010 | Intertherm P3RA-060K Air Conditioner
Sep 18, 2010 | Intertherm Air Conditioners
Dec 06, 2008 | Intertherm Air Conditioners
May 24, 2008 | Intertherm P3RA-048K Air Conditioner
Jan 15, 2008 | Intertherm P3RA-048K Air Conditioner
102 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: