Question about Heating & Cooling
Is the contactor engaging? Make sure it is getting 24v. If not, check the low pressure safety, outside thermostat (if you have one) and the defrost board. Follow the low voltage from the thermostat to all these controls, up to the contactor. Check the thermostat too. If you need a walk through I can help, if you have a volt/ohm meter.
Posted on Mar 02, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 07, 2016 | Intertherm Heating & Cooling
Sep 11, 2013 | Intertherm Heating & Cooling
Nov 02, 2011 | Intertherm P3RA-048K Air Conditioner
Dec 03, 2010 | Intertherm P3RA-060K Air Conditioner
Sep 18, 2010 | Intertherm Heating & Cooling
Dec 06, 2008 | Intertherm Heating & Cooling
May 24, 2008 | Intertherm P3RA-048K Air Conditioner
Jan 15, 2008 | Intertherm P3RA-048K Air Conditioner
103 people viewed this question
Usually answered in minutes!