Question about Refrigerators
Mitsubishi wall unit srk50zg condenser src50zg air con, new installation. Indoor unit works in cool mode (not as cool as it should be). Indoor unit does not operate on heat mode but the outdoor condenser does. The indoor unit does try to blow, no error codes or flashing lights. Fins on indoor unit move on cool but not on heat. Would lack of 410A give me this fault? I have been told to check valves around condenser. At this stage i am considering buying a new condenser just to get the job finished.
Double check your wiring .if the indoor fan is not blowing then you either have an electrical issue OR bad blower motor .
Posted on May 24, 2017
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: York Mini-Split Not Cooling? : (
This can only be a gas problem.
the split units goes on on and off if a shortage of gas is involved, the chances that you would here it wont be that big for the fans would make too much noise.
get a repair man for a re gas and all is well.
Posted on Oct 22, 2008
You may want to check that the pressure switch is not functioning? Secondly there is also a thermo sensor on the condenser coil which could be faulty.
Posted on Mar 04, 2009
My unit is giving me the same alarm. If you have found the solution, please email me at firstname.lastname@example.org
Thank you very much.
Posted on May 10, 2009
Please specify the make and model of your unit.
If this is a LG inverter model.
The six flashes of the indoor unit light indicates a CH 06 alarm.
This alarm state indicates that the indoor unit pipe temperature sensor has measured a temperature out of range or the unit is protecting itself from this low temp state. Indoor unit coil temperature to low. Should it have reached a temperature of -5°C for longer that 30sec it will switch the machine off.
It could indicate that the unit refrigerant charge is too low or the sensor has gone out of calibration.
It should measure 5kΩ @ 25°C
Posted on Mar 22, 2010
Here is where you can find all the info you will ever need about Mitsubishi Air Conditioning units...
Check out this tip that I wrote about that...
Mitsubishi Air Conditioner Troubleshooting and Repair
Posted on Aug 20, 2010
Tips for a great answer:
Apr 20, 2014 | Sanyo Split System Air Conditioner
Nov 28, 2013 | Air Con 9,000 Btu Split ditioner Wall...
Jun 18, 2012 | Viking Professional Series VCBB36 Bottom...
Jul 23, 2011 | Mitsubishi Mr. Slim MXZ30TN Air...
Nov 08, 2009 | Fujitsu 24C1 Air Conditioner
Aug 15, 2009 | Air Purifiers
Jan 22, 2009 | Heating & Cooling
657 people viewed this question
Usually answered in minutes!