Question about Amana PTH123B25AJ Heat Pump Air Conditioner
I have installed a new board. When the unit goes into heat the compressor come on with OS temp of 30 F. The compressor will run about 3-4 minutes and turn off, the heater strip then comes on and unit will cycle when the room reaches set temp.
I have replaces several boards over the years, my first RSKP0006 and never had this happen.
What's going on?
If the unit has an outdoor thermostat, this turns the aux. heat on very cold days. It may need to be replaced, or removed completely, if its kicking over to soon before it gets that cold. If its set to turn on the electric at 30 degrees, then its working the right way. Also, look for different temp. setting on the board you lust installed, there should be some sort of adjustment options on it. Especially if there is no thermostat outside.
Posted on Mar 05, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 11, 2015 | Refrigerators
Aug 08, 2007 | Emerson Quiet Kool 6GC53 Air Conditioner
Jan 12, 2011 | Ruud UAPA024 Air Conditioner
Aug 11, 2010 | Goodman CLQ36AR49 Air Conditioner
Aug 08, 2010 | Dometic Rooftop RV Air Conditioner
Jan 13, 2010 | Rinnai Heating & Cooling
Dec 17, 2009 | Humidifiers
Oct 17, 2009 | Goodman CLJ30AR32 Air Conditioner
Sep 01, 2009 | Chevrolet Suburban 1500 Cars & Trucks
Dec 15, 2008 | LG LP120HED Wall/Window Air Conditioner
Feb 02, 2016 | Amana PTH123B25AJ Heat Pump Air...
252 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: