Question about Amana PTH123B25AJ Heat Pump Air Conditioner
Heat pump would not work, repairman replaced and repaired a wire outside. Pump worked again until the middle of the night. I had the defrost board replaced last year, could this be it again? Repairman is coming again later, but am frustrated with this situation. Had to suffer through two cold nights and don't want another.
Repairman fixed a wire? sounds a little vague. If the outside coil is covered with ice, then it may be the board. Most defrost boards have a test terminal on them. Touch something to the test posts and see if the reversing valve switches on and the unit starts defrosting. If nothing happens, then its the board. There could be much more things causing it not to work, but I need more info.
Posted on Mar 05, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 12, 2015 | Coleman Heating & Cooling
Jan 03, 2014 | Heating & Cooling
Jan 07, 2010 | Carrier Heating & Cooling
Dec 12, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 17, 2009 | 1989 Jeep Comanche
Apr 04, 2009 | Ruud UBHC Air Conditioner
Dec 03, 2008 | Heating & Cooling
May 25, 2008 | Coleman Heating & Cooling
Nov 28, 2007 | Heating & Cooling
Feb 02, 2016 | Amana PTH123B25AJ Heat Pump Air...
96 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: