Question about Heating & Cooling
Try turning your thermostat from fan auto to fan manual, if the blower starts then you have a burned out speed on the heat leg.
If this is true, shut power off to furnace and try and trace out the blower motor wires. Usually they will
gto to a terminal block that is marked heat/cool.
Just reverse the connections
Posted on Feb 08, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 09, 2014 | GE Icp Heil 1/8 Hp Condenser Fan Motor...
Feb 28, 2014 | Heating & Cooling
Mar 06, 2013 | Electronics - Others
Jan 18, 2013 | Cars & Trucks
Aug 31, 2011 | Heating & Cooling
Dec 24, 2009 | Honeywell International Heil Quaker...
Nov 11, 2009 | Heating & Cooling
Jul 28, 2009 | Heating & Cooling
Jun 09, 2009 | Heating & Cooling
Dec 13, 2008 | Honeywell CT3200 5-2 Day Electronic...
202 people viewed this question
Usually answered in minutes!